Power factor: The power factor of an AC electric power system is defined as the ratio of the real power flowing to the load to the apparent power, and is a dimensionless number between 0 and 1 (frequently expressed as a percentage, e. g. 0. 5 pf = 50% pf). Real power is the capacity of the circuit for performing work in a particular time. Apparent power is the product of the current and voltage of the circuit. Due to energy stored in the load and returned to the source, or due to a non-linear load that distorts the wave shape of the current drawn from the source, the apparent power will be greater than the real power. In an electric power system, a load with low power factor draws more current than a load with a high power factor for the same amount of useful power transferred. The higher currents increase the energy lost in the distribution system, and require larger wires and other equipment. Because of the costs of larger equipment and wasted energy, electrical utilities will usually charge a higher cost to industrial or commercial costumers where there is a low power factor Linear loads with low power factor (such as induction motors) can be corrected with a passive network of capacitors or inductors. Non-linear loads, such as rectifiers, distort the current drawn from the system. In such cases, active or passive power factor correction may be used to counteract the distortion and raise the power factor. The devices for correction of the power factor may be at a central substation, spread out over a distribution system, or built into power-consuming equipment. Contents • 1 Power factor in linear circuits o 1. 1 Definition and calculation o 1. 2 Power factor correction of linear loads • 2 Non-linear loads o 2. 1 Non-sinusoidal components o 2. 2 Switched-mode power supplies o 2. Power factor correction in non-linear loads ? 2. 3. 1 Passive PFC ? 2. 3. 2 Active PFC • 3 Importance of power factor in distribution systems • 4 Measuring power factor • 5 Mnemonics • 6 References • 7 External links Power factor in linear circuits In a purely resistive AC circuit, voltage and current waveforms are in step (or in phase), changing polarity at the same instant in each cycle. All the power entering the loads is consumed. Where reactive loads are present, such as with capacitors or inductors, energy storage in the loads result in a time difference between the current and voltage waveforms. During each cycle of the AC voltage, extra energy, in addition to any energy consumed in the load, is temporarily stored in the load in electric or magnetic fields, and then returned to the power grid a fraction of a second later in the cycle. The “ebb and flow” of this nonproductive power increases the current in the line. Thus, a circuit with a low power factor will use higher currents to transfer a given quantity of real power than a circuit with a high power factor.
We will send an essay sample to you in 2 Hours. If you need help faster you can always use our custom writing service.Get help with my paper